In many hydroelectric projects there is a need to safely dissipate the energy associated with the elevation of the water surface. When the flow is not passing through the turbines, bypass valves are often used. A valve that is commonly used is the fixed-cone valve. Fixed-cone valves, also known as Howell-Bunger valves, are devices often used to safely reduce flow energy at dams with medium to high heads. The valve directs the outflow into a conical hollow jet, which requires a large area for energy dissipation. The flow is controlled by an adjustable sleeve, also known as the gate which surrounds the valve and requires minimal power for operation even for large valves. Depending on the installation, the conical jet may need to be controlled by installing a fixed stationary hood or other structure to contain and direct the conical jet. While the hood reduces the spray, the use of the hood causes the formation of a concentrated hollow jet having a high velocity. To eliminate the hollow jet and dissipate much of the associated energy, the hood can have interior baffles. If the hood is not precisely placed relative to the valve, a phenomenon, known as backsplash, will occur. Backsplash is when a significant amount of water exits the upstream end of the hood. Backsplash is a concern for operators because it can prevent access to the valve during operation and can flood valve vaults. Because the use of fixed-cone valves and baffled-hoods are becoming more popular, the need for guidelines to correctly position the hood relative to the valve will benefit both engineers and contractors. In some hydroelectric sites, submerging the fixed-cone valve is used to control the spray and dissipate energy. Submerging the valve can have can produce violent flow conditions which can cause damage to a structure or heavy erosion. The use of a submerged fixed-cone valve is rarely used, and a submerged valve used with a baffled-hood has never been constructed. The study performed shows that the use of a baffled hood with a fixed-cone valve in submerged conditions performs well. The results may lead the way for more submerged fixed-cone valves in the future.
|Advisor:||Johnson, Michael C.|
|Commitee:||Barfuss, Steven L., Caliendo, Joseph A.|
|School:||Utah State University|
|Department:||Civil and Environmental|
|School Location:||United States -- Utah|
|Source:||MAI 54/03M(E), Masters Abstracts International|
|Keywords:||Backsplash, Baffles, Cone-valve, Energy dissipation, Hood, Valves|
Copyright in each Dissertation and Thesis is retained by the author. All Rights Reserved
The supplemental file or files you are about to download were provided to ProQuest by the author as part of a
dissertation or thesis. The supplemental files are provided "AS IS" without warranty. ProQuest is not responsible for the
content, format or impact on the supplemental file(s) on our system. in some cases, the file type may be unknown or
may be a .exe file. We recommend caution as you open such files.
Copyright of the original materials contained in the supplemental file is retained by the author and your access to the
supplemental files is subject to the ProQuest Terms and Conditions of use.
Depending on the size of the file(s) you are downloading, the system may take some time to download them. Please be